SHX Series Circulating Fluidized Bed Boiler
Fuel: coal, wood, straw, and other biomass fuels.
SHX series boiler is a large capacity boiler, adopts the advanced technology of cyclone fluid combustion, cyclone separation structure & parametric design, and loop seal device, has advantages of energy saving, high thermal efficiency, sufficient output, and high steam quality. Moreover, the boiler could deal with the wastes (bark, waste wood material, black liquid) produced during paper processing through combustion, save operation cost.
Steam is necessary for paper processing industry. Usually, steam is used for drying to improve the strength and smoothness of paper. The water content of wet paper still as high as 53%~70% after squeezing, and it is not useful by using mechanical stress for anhydration, so, use cast iron dryer to dry paper, cooperate with the use of steam boiler. Except drying, it can also use for corrugated paper processing, andsupport the use of calender and glue paste roller.
Price of Paper Processing Industry Boilers
The price of paper processing industrial boilers is based on the capacity and accessories. Generally, the accessories of boilers include burner/grate, electric controller, steam header, water softener, BFW pump, platform ladder, and chimney, etc. If you would like to use the specific devices (brand, materials, quantity, etc.) or the additional equipment (air preheater, economizer, condenser, etc.), the prices are quite different. So, if you would like to get the exact price, please inquire for the details.
How to Select a Proper Boiler for Paper Processing Industry
1. Determine the capacity of the boiler. The boiler capacity should based on the Heating Load Curve or Heat Balance Diagram, and includes the heat loss in pipelines, self-used heat of boiler room, available used waste heat. While, usually, it is difficult to get the Heating Load Curve, the heating load could get based on the max thermal consumption per hour within production/heating/domestic, and then determine by using the coefficient.
2. Determine the boiler heating parameters, including pressure, temperature, etc.
3. Determine the boiler efficiency. In order to benefit for economic management, the boilers should have high thermal efficiency, and the boiler output, quantity and other performances have to adapt to the change of heat loading.
4. It is better to select the boilers with same capacity or combustion equipment. If different, the max limitation is two models, to decrease the problems of equipment layout and management.